|TD240 Master & Slave
|Page 1 of 1|
|Author:||RamonGC [ 22/01/2019, 21:52 ]|
|Post subject:||TD240 Master & Slave|
Hello, I'm using a TD240 as a master device in a modbus network with VFDs as slave devices.
My customer wants to integrate the system to a PLC they already have but the PLC is a Master device in another modbus network. Is there a way i can communicate the TD240 as a master device with a 3rd party PLC as a master device too?
I also have a EPL101 that i can use as an interface if needed.
|Author:||Pixsys tecnico 6 [ 23/01/2019, 9:59 ]|
|Post subject:||Re: TD240 Master & Slave|
it is possible if you use the EXP1 as Master mode and COM2 as Slave mode, but you need use the RS232 for the COM2.
|Page 1 of 1||All times are UTC + 1 hour [ DST ]|
|Powered by phpBB © 2000, 2002, 2005, 2007 phpBB Group